Thermal solar system
Free solar energy for hot water and heating.
ROTEX Solaris uses free solar energy and thereby supports the heating system. High-performance collectors from ROTEX own development and production are variable in installation and provide the highest energy efficiency.
For the health of your family
ROTEX thermal store with hygienic freshwater technology.
Perfect connection to different heating systems
For each roof
Possible as on-roof, in-roof or flat roof installation.
For all applications
Choose between efficient Drain-Back or flexible pressure solar system
ROTEX Solaris high performance solar collectors
The ROTEX Solaris offers a flexible solar thermal system providing water heating and space heating backup, to be used for pressurised solar and drain-back applications. The Solaris solar panels convert almost all of the shortwave solar radiation into heat through their highly selective coating. The three solar panel sizes and different assenbly types mean there is flexibility in adapting to roof characteristics. Since all buildings are different, there are various installation options for fitting the ROTEX flat solar panels onto the roof.
Maximum water hygiene day after day.
The ROTEX thermal stores were conceived in accordance with the latest thermal technology and water hygiene requirements. Its structure is fundamentally different from normal large volume hot water storage tanks. As a result of its design concept it delivers hygienically perfect hot water at any time. The actual heat is not stored in the domestic water itself, but in the storage tank water which is clearly separated from it. The optimum tank layering ensures that a supply of hot water is always available.
ROTEX Solaris solar panels - flexible assembly
The Solaris solar panels convert almost all of the shortwave solar radiation into
heat through their highly selective coating. The three different solar panel sizes mean there is flexibility in adapting to roof characteristics. Since all buildings are different, there are various installation options for fitting the ROTEX flat solar panels onto the roof. The solar panels can be fitted onto the tiles (on-roof ), into the roof (in-roof ) or also with a special substructure onto a flat roof.
ROTEX Solaris uses solar energy for water heating and effectively supports heating. In all ROTEX solar thermal stores, and the gas condensing/solar combination (GCU compact) and heat pump/solar combination (HPSU compact) with a storage tank volume of 500 litres, solar heating support has also been integrated ready for connection, alongside the solar hot water generation. If the solar heat is not consumed immediately, the ROTEX solar thermal store can store large volumes of solar heat and it is possible to use the heat for hot water or heating hours later or even the next day.
The perfect store for use with solar – the right temperature at every level
Solar collectors work more effectively the colder the water flowing through them. In solar thermal systems, it‘s important for the thermal store to achieve the widest possible thermal stratification. With the ROTEX thermal store, cool fresh water is fed into the corrugated pipe heat exchanger at the lowest point in the store. From here it travels upwards and is heated employing the instantaneous water heater principle. This ensures maximum cooling in the lower part of the store, from which the collectors are supplied with water. The degree of thermal stratification this creates in the ROTEX thermal store significantly increases the benefit to be gained from the solar thermal system as a whole.
ROTEX Solaris: 2 possibilities - always the first choice
ROTEX Solaris is available in two different variants, that meet all structural conditions and individual requirements.
1. The pressurised solar system (Solaris-P)
The pressurised solar system impresses with its simple installation
and is suitable for all applications and buildings. It operates efficiently and safely at any desired length of pipes and feed height. The well-engineered structure of the ROTEX solar thermal store means that an additional plate heat exchanger is not required. A bivalency heat exchanger for pressurised solar or other heat sources is already incorporated. That makes the system simple and flexible.
2. the direct Drain-Back system (Solaris-DB)
If the constructional conditions permit, we recommend the unpressurised and direct Drain-Back system. The water in the store is supplied directly and without heat exchanger to the solar panels, heated and then stratified into the store. This considerably increases the efficiency of the solar collectors and the entire utilisation of the installation. Since the system is unpressurised, components which would otherwise be required are not necessary, such as the expansion tank, pressure relief valve, pressure gauge and heat exchanger. The Solaris solar panels are only filled if there is enough heat from the sun and if the thermal store can absorb heat. The fully-automatic control system controls the system independently to provide optimum utilisation of the solar energy. If the sunshine is insufficient, or if the solar thermal store does not need any more heat, the feed pump switches off and the entire solar system drains into the thermal store. The addition of antifreeze agents is not required since the panel surface is not filled with water when the system is not operating. This is a further plus from the environmental perspective. The principle functions only if the connection pipes in the building and on the roof are installed with a constant gradient. If this is not possible, the pressurised solar system is the optimum alternative.
September 2015: Energiy efficiency label now also for heating
Individual heat generators will each bear a product label. The efficiency of a heating system depends not only on the heat generator, but on several components. That is why the combination or package label was introduced. This covers the heat generator plus other components such as the controller, cylinders, solar thermal systems and/or an additional heat generator. The combination label is calculated from the efficiency values of the individual appliances and devices. Hooking up a solar thermal system is the most effective way to reach a higher overall system efficiency class.