Owners and operators must ensure that repairs will prevent releases due to structural failure or corrosion as long as the UST system is used to store regulated substances.
The repair must meet the following requirements:
(a) Repairs to UST systems must be properly conducted in accordance with a code of practice developed by a nationally recognized association or an independent testing laboratory.
Note: The following codes and standards may be used to comply with paragraph (a) of this section: National Fire Protection Association Standard 30, “Flammable and Combustible Liquids Code”; American Petroleum Institute Publication 2200, “Repairing Crude Oil, Liquefied Petroleum Gas, and Product Pipelines”, American Petroleum Institute Publication 1631, Recommended Practice for Interior Lining of Existing Steel Underground Storage Tanks”; and National Leak Prevention Association Standard 631, “Spill Prevention, 10 Year Life Extension of Existing Steel Underground Tanks by Lining Without the Addition of Cathodic Protection.”
(b) Repairs to fiberglass-reinforced plastic tanks may be made by the manufacturer’s authorized representatives or in accordance with a code of practice developed by a nationally recognized association or an independent testing laboratory.
(c) Metal pipe sections and fittings that have released product as a result of corrosion or damage must be replaced. Fiberglass pipes and fittings may be repaired in accordance with the manufacturer’s specifications.
(d) Repaired tanks and piping must be tightness tested in accordance with 24.0742(3) and 24.0743(2) within 30 days following the date of completion of the repair except as provided in paragraphs (d)(1) through (3), of this section:
(1) The repaired tank is internally inspected in accordance with a code of practice developed by a nationally recognized association or an independent testing laboratory; or
(2) The repaired portion of the UST system is monitored monthly for releases in accordance with a method specified in 24.0742(4) through (8); or
(3) Another test method is used that is determined by the implementing agency to be no less protective of human health and the environment than those listed above.
(e) Within 6 months following the repair of any cathodically protected UST system, the protection system must be tested in accordance with 24.0721(2) and (3) to ensure that it is operating properly.
(f) UST system owners and operators must maintain records of each repair for the remaining operating life of the UST system that demonstrate compliance with the requirements of this section.History: Rule 3-01, eff 30 Aug 01.