Corona or Partial Discharge with Buzzing Noise
Corona can be visible in the form of light, typically a purple glow, as corona generally consists of micro arcs.
Darkening the environment can help to visualize the corona. We once attached a camera (set to a long exposure time) to a viewing window in a vacuum chamber to confirm that corona was indeed occurring, and thereby confirming our suspicions.
You can often hear corona hissing or cracking. Thus, stethoscopes or ultrasonic detectors (assuming you can place them in a safe location) can be used to find corona.
The corona discharges in insulation systems result in voltage transients. These pulses are superimposed on the applied voltage and may be detected, which is precisely what corona detection equipment looks for. In its most basic form, the following diagram is a corona (or partial discharge) measuring system.
When corona occurs it creates ozone (detrimental to the human lungs, eyes, etc.), ultraviolet light, nitric acid, electromagnetic emissions and sound.
Ozone is a strong odorous gas that deteriorates rubber-based insulation.
If moisture or high humidity conditions exist nitric acids can also be formed that attacks copper and other metals. The electromagnetic emission can be heard as interference on AM radios and the corona sound can be heard by the human ear and be ultrasonic scanning devices.
One important point to consider is that unlike infrared that detects heating due to current flow, corona indicates voltage problems and can be present without current flow. High potential in the electrical field is the major dictating factor for its presence.
Corona activity is at its strongest on the positive (+) and negative (-) peaks of the 60Hz cycle.
- Ultraviolet radiation
- Sound (hissing, or cracking as caused by explosive gas expansions)
- Nitric and various other acids
- Salts, sometimes seen as white powder deposits
- Other chemicals, depending on the insulator material
- Mechanical erosion of surfaces by ion bombardment
- Heat (although generally very little, and primarily in the insulator)
- Carbon deposits, thereby creating a path for severe arcing
How Corona works?
Focussing on corona discharge and surface discharge, i.e. electrical gas discharges occurring in ambient atmosphere, ionisation phenomena are initiated in the high electrical field region respectively resulting from the conductor geometry (wire, point, sharp edge) or from a triple point (metallic conductor / insulation material /gas).
In any case, electron in elastic collisions will also lead to gas molecules dissociation and excitation resulting in chemical active species formation and light emission; elastic collision between ions and neutral molecules will result in local gas heating.
Light, gaseous chemical reactants and heating are consequently evidence of gas discharges.
- Corona and Tracking Conditions in Metal-clad Switchgear Case Studies By James Brady, Level-III Certified Thermographer
- CHARACTERIZATIONOFMEDIUM VOLTAGE EQUIPMENT AGEING BY MONITORING OF PARTIAL DISCHARGES CHEMICAL AND ACOUSTICAL EMISSION E.Odic*, E.Jouseau**, G. Vivien**, C-S.Maroni**