The fully self-contained KCG598E provides precision protection against malfunction and human and operational hazards under loss of mains conditions.
The DIN rail mounted digitally controlled unit meets the protection requirements for generators connected to mains supply, such as defined in the G59/2 and similar recommendations.
Less wiring, no extra modules. Operating mode is selected by simple auxiliary contacts on the generator breaker and on the mains breaker. LEDs and open collector outputs indicate operating mode and žFirst UpÓ cause of trip.
State-of-the-art digital technology throughout, with quartz-controlled Loss of Mains detection. True RMS
Self powered from monitored voltage input:
100-120, 200-240, 380-415 or
Latching relays as standard.
User selectable to 3-180sec auto reset of alarms
100VA -250V/2A max.
50W -100V/1A max.
30V DC max. - 500mA max.
An independent watchdog monitors signal flow. Flashing of LEDs1, 2 and 3 in a binary pattern indicate operational error
Class HUE, (DIN40040)
-20 to +70oC
Flame retardant polycarbonate to UL94 (VO) measurements.
Loss of Mains Protection KCG598E will provide the following protection:
- 2 stage Over and Under Voltage - 2 stage Over and Under Frequency - Rate of Change of Frequency ( ROCOF, df/dt ) - Vector Shift (step phase angle) - Voltage Imbalance