Have him recover the refrigerant and weigh in the proper charge. Ask him to warm the accumulator to be certain all refrigerant is removed. The check chart is just that - for checking. If you read the instructions for charging the unit it will tell you not to use the chart to adjust the charge.
Should have him adjust the charge in cooling mode based on SC, and operation verified by checking superheated.
Climate Control Solutions for your Home or Office
Serving Northeast Philadelphia and Surrounding Areas