• C-UL LISTED
• GFCI Class A, 5mA trip level
• GFCI disconnects line & neutral (L2)
• 2-year manufacturer warranty
• In-floor sensor or regulator
• Dual voltage 120V or 240V
• Output relay 15A
• Screw terminals
• Easy switching between °F and °C
• Large back-lit display for easy read-out
The heated floor thermostats are delivered with factory-set programs as follows:
ADDITIONAL THERMOSTAT FEATURES:
Ground Fault Circuit Interrupter (GFCI):
The radiant floor heating thermostat has an integrated Ground Fault Circuit Interrupter (GFCI, Class A). In case
a ground fault should occur, the thermostat will disconnect both lines to the
floor heating element. The
thermostat and the GFCI are dual voltage models suitable for 120/240V 50/60 Hz supplies.
The thermostat's set-point can be
adjusted, matching the actual floor temperature. This ensures a 100%
actual measurement and control of your underfloor heating system.
The thermostat controls floor
temperatures from +41°+104°F. The scale can be adjusted if desired
within this temperature range.
The temperature can be temporarily changed for a single event.
The comfort mode temperature is reset at the next event, and
the thermostat will return to the scheduled event, previously programmed by the
The thermostat's scheduled event program can be cancelled if needed (I.e., during
holidays or vacations). For example, to protect against frost or freezing while
you are gone, the temperature can be adjusted to 41°F
(5°C). The new setpoint remains valid until the
thermostat's manual mode is cancelled.
Monitoring of energy consumption:
Total switch-on time in percentage can be read within the
latest 2 days, 30 days, or 365 days. This facilitates energy-efficient operation
by allowing the heat
consumption to be controlled.
All settings and the clock are maintained in case the floor heating thermostat
is switched off on the GFCI test button. If the main
power supply is interrupted for more than 10 hours, the current
time and date must be reset.
Mounting of floor sensor:
The floor sensor is used for comfortable heating of the floor. The
sensor is mounted in conduit for replacement purposes. The
conduit is placed between radiant heating cables and is ended
towards the floor surface. If required, the sensor cable may be
extended up to 300 ft. (100 m.) with standard installation cable.
The thermostat is an electronic on/off thermostat for controlling
temperature by means of a sensor placed externally. The heat output
is switched on and off with a difference of only 0.7°F (0.4°C).
The thermostat can be configured for
control of floor temperature and regulator without sensor. It is compatible with existing floor
sensors by means of a temperature setting, making it the best
thermostat for renovation purposes.
According to the following standards:
GFCI: UL 943:1993
Thermostat: UL 8730-2-9:1998
UL file number: E157297.